Tel: 0551-62798880 Fax: 0551-62798890 Domestic Sales Department: 0551-62798833 133-9551-2908
Headquarters address: 27/F,Block D,NO.660, Green Land Yinghai, Ma'anshan Road S.,Hefei, Anhui, China.
FDGL Pulse Bag Filter for Thermal Power Plant
The series of FDGL bag filter for thermal power station is designed on basis of our long term experience on designing and developing furnace bag filter and the thermal power station’s special condition. Compared with electric-static dust collector, FDGL bag filter has many advantages, such as: better efficiency, smaller in size, cheaper, low operating cost, offline dust cleaning,online or offline inspection, high automation, high temperature resistance filter media, etc. Take for the situations of heavy oil ignition, incomplete burned fuel,boiler tube explosion. The self inspection and control system are enhanced to ensure the equipment long term operation.
The working process of the bin type pump is divided into 4 phases:
1. Feeding phase
When the feeding valve is opened, the materials fall in the pump body freely. When the rising materials in the pump body touch the level gage, the level gage gives out the full-material signal, and the feeding system is closed automatically to complete the feeding process.
2. Fluidifying and pressing phase
The air inlet valve is opened automatically, the compressed air enters the bottom of the pump body, and is diffused through the fluidized bed. With the full fluidization of the material, the gas inside the pump rises.
3. Conveying phase
When the pressure inside the pump reaches a certain value, the pressure sensor gives out a signal, the discharge valve is opened automatically, the materials on the fluidized bed are conveyed, the materials inside the pump decrease gradually. In this process, the materials on the fluidized bed are fluidized and conveyed simultaneously.
4. Blowing phase
When the materials inside the pump are conveyed completely, and the pressure drops to pipeline resistance, The indicator light gives out a signal. The air continues to be taken in for a given time. Compress the air, and clean the pipeline. And then close the air inlet valve at a regular interval, close the discharge valve, open the feeding valve and complete one conveying cycle.
The above processes are performed automatically.
Process Air Volume: 7~3,600,000m3/h,satisfy the needs of 600MW motor
Dusty Gas Temperature: Normal140~160℃,transient temperature
Emission Concentration: ≤30mg/Nm3
Equipment Resistance: ≤1500pa
Filter Bag Service Life: 2~4years
Filter Body Pressure Load: 5000~12000Pa
Dust Convey Method: Mechanical or air-operated